PFP Pipe Closer - 200mm, Depth 60mm
CE Marked | Certified for PVC-U, PVC-C, PE, LDPE, MDPE, HDPE, ABS, SAN+PVC and PP pipes | Fire classifications up to 240 minutes for both integrity and insulation.
About the PFP Pipe Closer Product
PFP Pipe Closers are designed to maintain the fire resistance of fire rated walls and floors where these are breached by continuous plastic pipes. The PFP Pipe Closer can be used in gypsum, masonry and concrete walls and with concrete floors.
Each pipe collar consists of a Silver coated circular steel shell that splits in two to fit around the service penetrations by means of a simple slide-lock system. The steel shell contains a graphite based reactive material which reacts when exposed to heat closing the openings left by the softening plastic pipe in fire.
When testing pipes, one can choose not to cap (or close) the pipe, or cap the pipe inside the furnace, or outside the furnace, or on both sides. The configuration chosen depends on the intended application of the pipe and/or the installation environment. The code defining if a pipe is capped is stated after the fire classification. For instance EI 60 C/U which means the pipe was capped inside the furnace, and uncapped outside the furnace. The test configuration defines the approvals possible.
For more information please download the Product Data Sheet under the Fire Test Reports
Product Size Availability
PFP Pipe Closer: Size: 200mm x Depth: 60mm - Colour Red
For more sizes click here
We have technical representatives who provide assistance in the selection and specification of the products on this site and should be consulted for exact installation and product suitability. Ensure an early engagement with ourselves, designers, main contractor and specialist installers before any installation. Other trades and/or manufacturers may need to be consulted. For in-depth information, specification and technical advice please call our Head Office on Tel: +(0)1329 841416 or email firstname.lastname@example.org
All interested parties, designer, specifier, main contractor and specialist installers should provide access to allow the fire stopping seals to be regularly inspected and maintained, as well as records kept of such maintenance at minimum periods of 12 months, as required by the Regulatory Reform Order, and repaired if necessary. Reference should be made to ASFP TGD 17 Code of Practice for the Installation and Inspection of Fire Stopping.
It is vital that those entrusted to design or install a fire stopping product have the necessary levels of competence to undertake the task professionally and thoroughly. The level of competency required will be commensurate with the expected complexity of the building. All designers must eliminate, reduce or control foreseeable risks that may arise during installation, construction or maintenance when preparing or modifying designs. Clients should ensure that the principal designer and principal contractor carry out their duties under CDM regulations. The ASFP foundation course in passive fire protection provides essential knowledge as part of demonstrating competency and understanding in this key fire protection specialism.
Please refer to the ETA sheet for fields of application for this product. For further information on installation requirements please refer to the pipe manufacturer data and wall specification to ensure the compatibility of this product, if in doubt please contact the technical team with services and wall specification on Tel: +(0)1329 841416 or email email@example.com
Fire Test Reports
Download the following PFP Pipe Closer Product Data Sheet (PDS), Safety Data Sheet (SDS), Technical Data Sheet (TDS), Declaration of Performance (DoP), Certificate of Constancy of Performance (CoC) & European Technical Assessment Sheet (ETA).
Type:Fire Pipe Collar
As part of our policy of ongoing improvements, we reserve the right to modify, alter or change product specifications without giving notice. Product illustrations are representations only. All information contained in this document is provided for guidance only, and as Intumescent.com (part of the Stormflame Group) has no control over the specific application or installation methods of the products, or of the prevailing site conditions, no warranties expressed or implied are intended to be given as to the actual performance of the products mentioned or referred to, and no liability whatsoever will be accepted for any loss, damage or injury arising from the use of the information given of products mentioned or referred to herein.
The above information to the best of our knowledge is true and accurate and based upon current test data and is supplied for your guidance only. Customers should satisfy themselves to the suitability of the product based on the products limitation of applications and that the product is fit for purpose for their intended use and no guarantee is given or implied since the conditions of actual use are beyond our control. Intumescent.com (part of the Stormflame Group), disclaim any liability for loss, damage or other expense arising from the use of information, data or products mentioned or referred to and reserve the right to change any details or specifications without notice. If you are in any doubt as to the suitability of this product for your intended application please contact our technical team on 01329 841 416 or email firstname.lastname@example.org and we will contact you.